- Резервуар представляет собой стальной, сварной, горизонтальный, цилиндрический сосуд с конусными отбортованными днищами, кольцами жесткости и одной горловиной с крышкой, имеющей сливо-наливную трубу и смотровой люк, дренажный патрубок и штуцер с указателеРезервуар представляет собой стальной, сварной, горизонтальный, цилиндрический сосуд с конусными отбортованными днищами, кольцами жесткости и одной горловиной с крышкой, имеющей сливо-наливную трубу и смотровой люк, дренажный патрубок и штуцер с указателе
The tank represents a steel, welded, horizontal, cylindrical vessel with the conical otbortovanny bottoms, rings of rigidity and one mouth with the cover having a slivo-bulk pipe and the viewing hatch, a drainage branch pipe and the union with the index of level.
Rules of transportation, storage and operation.
In transit the tank has to be fixed reliably on vehicles by means of multireverse fastenings, bars laying, wedges, cables or a wire. At the same time mooring of the tank has to be made on cargo and transport brackets.
During the loading and unloading works of a zastropk of the tank has to it is made for cargo brackets.
Cargo operations with the filled tanks, and also dropping the tank or free rolling on sloping are strictly forbidden either to unloading from vehicles or installation in a ditch.
Rolling the tank (at uncovered a mouth with the equipment) is allowed only in field conditions with an obligatory pritormazhivaniye of the tank and respect for precaution from injury of a mouth and the acting details.
Movement of the tank has to is made by means of cargo cranes. Movement of the tank on wooden linings is allowed (sloping). At the same time precaution from injury of a mouth, branch pipes, etc. details has to be observed.
The tank to be stored on the open area. The platform has to be equal, settle down in the dry place with strong soil and have a bias for a water drain. The tank has to be laid on the wooden linings excluding contact of its surface with grunoty.
During loading unloading and the equipment of the platform for storage placement of the tank on soil without linings is allowed temporary (about one month).
At transportation, storage and operation the mouth and hatches of the tank have to be densely closed by covers, and branch pipes - caps.
In sealing connections there have to be laying.
At statement of the tank on the storage all the neozinced and unpainted surfaces have to be preserved. For preservation of the neozinced internal surface of the tank 30% solution of conservation NG-203 oil in accordance with GOST 12328-77 or the additives AKOR-1 in accordance with GOST 15171 in diesel fuel in accordance with GOST 4749-73, and are applied to preservation of fasteners and chains - PVK greasing in accordance with GOST 19537-74.
At operation the tank can be installed on wooden laying in field conditions, on bulk sandy pillows or directly on soil is opened or in a ditch. The order of installation is defined by the corresponding managements and projects of objects. Laying should not settle down under welded seams of the tank.
At placement of the tank on a sandy pillow, adjoining to soil, the part of the tank has to become covered by anticorrosion isolation (a primer, bitumen).
At installation of the tank in a ditch with the subsequent filling by soil its all external surface has to be covered with the specified isolation.
Installation of the tank on soil and in earth shelter without isolation is allowed only in field conditions.
At operation the tank has to be grounded.
During the filling or depletion of the tank it is necessary to open a drainage branch pipe. Before measurement of level of oil products the stopper of pressure relief has to be unscrewed on height providing the message of a cavity of the tank with the atmosphere through an opening in a stopper.
Blows to a surface and details of the tank or other influences causing mechanical damages and violations of coloring (at casual damage of coloring measures to its restoration have to be taken) are not allowed.
At transportation, storage and operation of the tank the safety regulations and fire-prevention requirements existing on object have to be carried out.