Precision Emerson HSC conditioners (Mini CabinetCooler)
Systems for telecommunication stations and remote communication centers
The present of a design and components, such as the spiral compressor, centrifugal fans, the mode - natural cooling, reduce energy consumption of the block and significantly reduces operational expenses.
Mini Cooler blocks represent internal complex conditioners of direct action with the built-in condenser of air cooling, are specially intended for installation in telecommunication cases or containers (BTS containers and other technological volumes).
High density of power
The increasing and bigger number of devices of technical support of modern telecommunication networks is installed in the small rooms demanding the high power of cooling at the small sizes of the conditioner. Mini Cooler blocks are developed for ensuring high power of cooling (to 5 kW) at the sizes of the case of only 310х620х1595 mm.
The evaporator fan, the drive of the gate and control system in case of interruptions of network power supply receive food from emergency sources 48B of a direct current. Continuous ventilation and strengthening of the mode of natural cooling ensure trouble-free operation of the capital telecommunication equipment. Food 48B of a direct current passes service life and increases reliability of microprocessors and the block.
Speed of commissioning
The Hladagentny contour is delivered filled, carefully adjusted and completely tested. It is not required to carry out any pressure tests on an installation site. Installation process in addition accelerates due to use of special electric sockets (on demand) the program of automatic self-testing. Process of installation and testing is completely carried out less than in 25 min. and does not demand participation of specially prepared personnel.
For optimization of the air stream directed to the condenser in the mode of direct mechanical cooling specially developed air-ventilation chamber which will also allow to reduce noise level is offered, to avoid cycling of streams of air and will prevent hit in the moisture block.