- Country of manufactureRussia
- PurposeIndustrial wastewater
- Cleaning methodBiological
Ochistnyesooruzheniya from 4 to 10 m3 / day
Air Master - are modular structures for local treatment podzemnoyustanovki capacity from 4 to 10 m 3 / day. The combination of biological treatment ihimicheskoy produces guaranteed results bolshomukolichestvu parameters, as well as significantly reduce the size and cost of ochistnyhsooruzheny.
Preimuschestvaochistnyh facilities Air Master
· Full operational readiness
· Stable performance when loading 5 - 10%
· Sanitary protection area of 15 m
· There are no restrictions on the dumping of domestic garbage
· Reliable automatic
· Does not require the presence of technical staff (SMS notification)
· Possible volatile mode
· Phosphorous removal from Photo
· Possible flooding
· Life of 60 years
Installing Air Master obespechivaetekologichnoe and reliable solution to the problems with wastewater treatment for:
· Hotels, boarding houses, complexes of residential buildings;
· Cottage villages, neighborhoods;
· Office buildings, schools, kindergartens.
Sewage treatment plants do not give vrednyhvybrosov into the atmosphere. On the permitted discharge of treated water Stacee and obezzarazhennyhstochnyh on terrain and bodies of water (if installing UV).
Maksimalnyyzalpovy discharge 3.6 m³
Performance: 8 m³ / day
Height: 2825 mm
Kolichestvopolzovateley: 40 people
Pros Air Master 40
· No need to install additional wells in the area.
· A more effective solution for houses, around which the relief does not allow vodevyhodit gravity.
· Harmonious design of the system performance, "green up" fits well vlandshaft infield.
· Samotechny release purified water is not limited in time rezhimeprostogo settler without an external power supply.
· Light weight, easy transportation and installation.
· Recirculation of purified water, no permanent residency required.
· The addition of the coagulant, increased deposition rate of suspended solids, phosphorous removal from the effluent.
· Improved power connection system.
· There is no limitation on dumping waste (cloth, food, etc. ).
· System of external fins, reliable protection from the station housing deformatsiipod exposure of groundwater and soil seasonal movement.
The treatment plant 40 Robust Air Master absorption compulsory field or fields filtering equipment, water sbrosochischennoy can be arranged directly on the ground or in drenazhnyei stormwater system.
Maintenance intervals once a year.
Outside the settlements, instead, where there are no engineering Water supply and sewerage network, dlyaochistki wastewater from individual buildings using local ustanovkiochistki wastewater. Installing Air Master 40 for komfortnogoprozhivaniya 40 people and provides an eco - friendly and reliable solution to the problems sochistkoy wastewater to one or a group of cottages. Apparatus according obrabotkestochnyh water Air Master fields 40 is substitute filtering and (or) the irrigation of fields occupying a large area. Purified water from the installation Air Master 40 mozhnonapravlyat a surface irrigation system or directly into the duct (ditch) (provided UV setting).
The stations are designed for the biological purification stochnyhvod having the following characteristics:
The unit provides clean household stochnyhvod to standards - compliant SanPiN184.108.40.2060 - 00 "Gigienicheskietrebovaniya to surface water protection"
Estimated harakteristikistochnyh water entering the treatment plant:
Temperaturanemenee 15 of Si is not more than 25 of the C
BOD 5 is not more than 350 mg / l
HPKnebolee 525 mg / l
Suspended veschestvanebolee 260 mg / l
Concentration NP≤12 mg / l
pHne less than 6.5 less than 8.5
Harakteristikastochnyh water outlet:
Concentration VV≤0,25 mg / l
Concentration NP≤0,05 mg / l
BPKpoln≤2,0 mg / l
HPK≤15 mg / l
pH6,5 - 8,5
Helminth eggs, virusynet
Wastewater entering the station dolzhensootvetstvovat its performance.
Permitted discharge of treated at the station and obezzarazhennyhstochnyh water on terrain and water bodies in compliance with the requirements SanPin220.127.116.110 - 00.
Sewage treatment plants do not produce harmful emissions in the air.
These parameters are observed when polnoykomplektatsii stations, including ultraviolet disinfection unit.
MPC rybohozyaystvennyhvodoemov 1 category:
BPKpoln3mg / l
HPK15mg / l
Suspended veschestva0,25mg / l
PAV0,1mg / l
Nefteprodukty0,1 mg / l
Helminth eggs, virusynedopuskayutsya
pH6,5 - 8,5
Opisanieraboty Air Master 4 0
Inside the wastewater system is two - chamber settling tank bioreactor with a submerged loading laminar settling tank, coagulation system, system sludge decontamination pumps for clean water, sewerage sooruzheniyaoborudovano ventilation pipes for connecting the riser ventilation (at otsutstviityagi in the supply sewer network) and mounting loops fiksatsiiochistnogo construction on a concrete slab.
The treatment plant comes fully stocked and ready kmontazhu module.
All components and parts kontaktiruyuschieso wastewater, made of corrosion impervious materials: polypropylene, polyethylene, polyvinyl chloride, silicone. The design of the treatment plant rasschitanana uneven delivery of waste water during the day time with the coefficient srednesutochnoyneravnomernosti consumption not more than 2.
The Air Master realized environmentally clean technology deep biohimicheskoyochistki wastewater biocenoses attached and freely floating avtotrofnyhi heterotrophic microorganisms acting under aerobic and anaerobic conditions, with automatic maintenance of the concentration of activated sludge in the aeration tank ipervichnom settler, as well as long - term stabilization of excess sludge sposleduyuschimi processes after - treatment and decontamination .
Stoke enters the receiving chamber drive, where accumulation nerastvorimyhvzveshennyh substances discharged with wastewater. Simultaneously, in the anaerobic denitrification processes kamereproiskhodyat aimed izstoka nitrogen removal. Overflow chamber drive located so that waste vodyprotekali at the lowest rate, whereby each chamber proiskhoditosedanie coarse particulate matter to the bottom.
From the receiving chamber drive gravity flow enters the upper portion biofiltrai uniformly distributed over the entire area of the biological loading and nasyschayutsyakislorodom. A biological filter (biofilter) - structure, wherein stochnayavoda filtered through the feed material coated with a biofilm (biofilm) formed colonies of microorganisms. The biofilter installed aeratsionnyyelement intended to force the saturation of water with oxygen izvozduha. This also served Eco Membrana precipitating drug in a liquid formulation fraktsii. Osazhdayuschy dosed strictly according to realnoyproizvoditelnostyu WWTP. Task precipitating drug provestihimicheskoe binding phosphate present in the effluent, as well as uluchshiteffektivnost precipitation in the subsequent chamber sump laminar.
In operation, a spent bioreactor and dead biofilm (excess sludge) washed off and removed from the biofilter at the bottom of the chamber body, as well as precipitated NADH laminar settling. The excess sludge is removed from pomoschyugidravlicheskoy sludge collection and recovery system ochistnogosooruzheniya into the receiving chamber, where the process of its stabilization and mineralization.
Air Master is programmed on circadian cycle of operation and during periods naimenshegopostupleniya Photo via hydraulic sludge collection and recovery system, provides stable Incoming podderzhaniyazhiznedeyatelnosti nutrients for the biomass through the sludge recycling.
The system employs designed and patented hydraulic sistemasbora and removing sediment. With this system, a treatment plant realizovansamobalansiruyuschiysya mechanism for maintaining the concentration of the activated sludge - vaerotenke biofilter. Collection and disposal of sludge is working on the program, uchityvayuscheysutochnuyu uneven flow proceeds.
Stock from the bioreactor enters the chamber laminar settler where proiskhodituderzhanie suspended particles contained in the effluent, as well as particle otkreplennoybiomassy denitrification process along with the flow. High effektivnostlaminarnogo sump allows for high performance cleaning stokaot suspended particles. Detained precipitate with predvaritelnonitrifitsirovannym drain is sent to the camera drive. Vzveshennyhchastits deposition in laminar flows to the sump 4 times more effective than obychnomotstoynike.
Purified water enters the clear water chamber, wherein the pump installed dvavysokoproizvoditelnyh - primary and backup organized in gruppuKNS. The pumps are running at a time, producing a uniform resource.
The pumps are designed for discharging treated water from the treatment plant, water libopodachi BioClean ultraviolet disinfection unit for dalneysheyobrabotki (optional). UV disinfection allows prakticheskipolnostyu destroy pathogens. The bactericidal ustanovkahprimenyayutsya continuous UV radiation sources, kotoryevozdeystvuet in the aquatic environment via a special material in a range of lengths voln180 - 300 nm. For messaging and remote control operation ochistnyhsooruzheny and for the timely prevention of emergency situations, the station vozmozhnooborudovat system of SMS alerts and remote control rabotoyochistnyh facilities.
This system monitors the presence of external power supply, nalichiyahimikatov, temperature control, signals the need for sludge pumping, protects the equipment against leakage and the flooding chamber.
Also, remote control of the system power supply, on / off and emergency backup pumps on / otklyucheniezvukovoy / light alarm.
|Maximum volley reset m³||3.6|
|Capacity, m³ / day||8|
|The number of users, persons:||40|
|The size of the base, mm||4000h2120|
|Throat diameter, mm||1h630, 1h1220|
|Depth / Log diameter, mm||355|
|Area for installation, m²||8.5|
|Compressors x pumps pieces.||1/3|
|Photo hourly average flow m³ / h||0.33|
|Installed power, kW||1.25|
|Power consumption in kW / h||0.27|
|Recommended settings of the supply electric cable||3h2,5|
|Maximum operating weight, t||16.8|