- Country of manufactureBelarus
- Type of refrigeratorBilocular
The case refrigerating two-chamber is intended for storage and sale of foodstuff at trade enterprises and public catering, etc.: in the refrigerator - cooled, in a low-temperature chamber - frozen.
Conditions, periods of storage of perishable goods have to correspond specified on packing.
In a case installation site air temperature from plus 12 to plus 30 °C and relative humidity to 80%. At a temperature of air above 30 °C of coefficient of working hours can reach to 0,95.
Temperature in the net volume of the refrigerator has to be from 0 to 6 °C, in the freezer from minus 12 to minus 6 °C.
Optimum work of a case (the stable set temperature in case chambers, the smallest expense of the electric power, coefficient of working hours to 0,75) is carried out at an air temperature to plus 25 °C. At more high temperature installation of conditioners is necessary.
The refrigerator two-chamber can be to a chamber izgotovlen:oba low-temperature, or both refrigerators. External sheets of panels are made of the sheet metal processed by a corrosion-resistant coating and painted or stainless steel.
Main technical characteristics of a case refrigerating
Device and work of a case
The case represents the national team from a sandwich panels a design. In a case there is a vertical partition (thickness of 60 mm) which divides a case into refrigerating (HK) and freezing (MK) of a chamber. Cooling is carried out by an air cooler in MK and an air cooler in HK. Air coolers are closed by protection plastic covers with the built-in fans for hashing of air in chambers.
Ottayka of an air cooler of MK happens to the help of TENA located under it. Ottayka of an air cooler of HK occurs in the natural way, thawed snow is removed from chambers on tubes and flows down in the collection of thawed snow located under the case bottom.
Control of the Thawing mode is exercised in certain time according to the program from the processor for each chamber.
Processors are installed on the forward panel of a case at the left and on the right. Refrigerating units, consist of the compressor and the condenser and ventilatory knot of import production located above a case. There is an automatic switch for protection of elements of an electric circuit.
Doors of chambers open independently from each other. Sealing of a doorway is carried out by means of magnetic consolidation on all perimeter of a door.
Lighting of cameras is carried out by means of luminescent lamps which turn on automatically when opening the corresponding door. Lamps, at desire, can be switched-off the regular switch and they will not turn on when opening a door.
On the front panel the light-signal fittings, switches of refrigerating units, microprocessors operating operation of refrigerating units are located. According to the program put in microprocessors there is a turning on shutdown of refrigerating units for maintenance of necessary temperature in cameras of the refrigerator, turning on of fans of an obduv of air coolers, and also inclusions TENOV for an ottayka of snow cover of an air cooler of the freezer.In a case regiments lattices for an arrangement of products are located. Regiments removable can be also rearranged on height. In the lower part of a case there is a starting pallet for collecting thawed snow. Four support regulated on height which allow to correct roughnesses of a floor are fastened to the bottom of a case.