Cables for the security and fire alarm system to buy in Kiev at the best prices!
Not extending burning, not containing halogens, screened install cable. Static shielding protects from pulse hindrances.
• Isolation maintains FE180 180 min. Test in sootv. DINVDE0472 part 814, IEC60331 at direct influence of a flame of 180 min.
• E 90: maintains at least 90 min. Test in compliance of DIN4102 part 12. Reliable working capacity within 90 min. systems of water supply at the fire, systems of providing with air and withdrawal of a smoke and heat from an emergency exit, and also other constructions of protection against the fire in hospitals and special fire elevators.
JE-H (St) H FE180 cable: design
Vein - the monolithic copper conductor.
Isolation - a special impregnating agent - the structured fireproof polymer according to the VDE 0207 standard.
Internal cover - fireproof material.
Eran - aluminum foil.
Cover - a stukturirovany fire-resistant, halogen-free polymeric compound of orange color according to the VDE 0207 standard.
JE-H (St) H FE180 cable: application
Not extending burning, not containing halogens, screened install cable with the improved pozharostoykost for information transfer, the measuring purposes and signaling. Static shielding protects from pulse hindrances. At the fire do not emit korrizionny gases. Are applied to laying in constructions, in special cases laying in free space is allowed, however at additional protection against sunshine. The install cable is recommended for continuous laying in fire hazardous zones, in dry and damp rooms, and also under plaster.
Structure of the JE-H (St) H FE180 cable
naked copper conductors diameter are 0,8 mm
isolation of veins from the special winding which is not containing halogens, shity polymer in compliance of DIN VDE 0207 part 23, HI2 not extending burning
designations of veins by means of rings in sootv. DIN VDE 0815
veins are twisted in couples, 5 couples in a plait - special
winding from polyester and fiber glass
the screen from the aluminum foil covered with synthetic material with the additional conductor
the external cover, free from halogens, which is not extending burning the HM2 DIN VDE 0207 type part 24